Geson Air Cooled Chiller: The Ultimate FAQ Guide
Have you been searching for a reliable refrigeration system?
Need something for the dehumidification of air?
Or you need help cooling fluids in your different settings?
Your answer is here – An air cooled chiller.
Geson Chiller is one of the top air cooled chiller manufacturers.
Air Cooled Scroll Chiller Manufacturers and Air Cooled Scroll Chiller Manufacturers.
Here, you will get the complete guide regarding air cooled chillers.
Air Cooled Scroll Chiller Manufacturers
What Does An Air Cooled Chiller Mean?
Figure 1: An Air cooled chiller
An air cooled chiller is a system for dehumidifying air and/or cooling fluids.
You can utilize it in both industrial and commercial facilities.
How Does An Air Cooled Chiller Work?
Air cooled chillers function by absorbing heat from process water.
It then transfers it to the air surrounding the chiller unit.
This Air Cooled Chiller Working is suitable in applications where the discharge of extra heat isn’t a problem. Rather, it offers some benefits.
For example, you can use the extra heat produced in warming a specified area during winter.
This saves costs compared to traditional heating systems.
Air Cooled Chiller Working Principle
What Differentiates An Air Cooled Chiller From A Water-Cooled Chiller?
Air cooled chillers come with a condenser, and it gets its cooling from the air in the environment.
You can use them for medium and small installations.
However, due to recent improvements in their structure, you can use them for large installations as well.
Water-cooled chillers, on the other hand, feature water-cooled condensers.
These condensers have a cooling tower.
They work well for large and medium installations where there’s enough water available.
Water-cooled chillers are also useful where there’s a need for the system to perform constantly, without the ambient temperature.
This is because fluctuations in the ambient temperature do not affect the capacity of water-cooled chillers.
Do Air Cooled Chillers Require Cooling Towers?
An air cooled chiller can make use of your open spaces like roofs, parking lots, or any area with ground level.
Therefore, there’s no need for you to get cooling towers, in contrast to water-cooled chillers that require them.
Water Cooling Tower
Where Can I Use My Chiller?
Chillers cool items by emitting high-heat such as lasers and MRI machines.
Air cooled screw chiller manufacturers said that you can use them on campuses, hotels, and hospitals.
Also use them in restaurants, manufacturing, and industrial plants, corporate events, and sporting events.
Industrial Water Chiller Application
What Gas Can I Use In My Chiller?
Concerning the low-medium capacity chillers, you will need to make use of R-407C and R-410A.
For larger applications, you should use R-123 and R-134a.
You can get more choice from air cooled screw chiller suppliers.
Which Is Better: Air Cooled Chillers Or Water-Cooled Chillers?
Water-cooled chillers are better because they feature a cooling tower, which is absent in air cooled chillers.
With this, you will get more efficiency from water-cooled chillers.
Air Cooled Chiller Vs Water Cooled Chiller (2)
What Are The Benefits Of Utilizing Air Cooled Chillers?
Some of the benefits of air cooled chillers include low maintenance costs, no water costs, especially in the cities.
Others include easy operation, cooling towers absent, and no water issues to deal with.
What Is The Right Temperature For An Air Chiller?
Generally, for cooling equipment, temperatures that fall within 45 – 60 degrees are okay.
However, for pharmaceutical reasons, the recommended temperature should be within 35 – 46 degrees.
Air Cooled Chiller Kw/ton is different at different temperatures.
Pls consult the air cooled screw chiller suppliers.
Chiller Temperature Setting
What Are The Major Components Of An Air Cooled Chiller?
The main components of an air cooled chiller include the condenser, condenser fans, compressor, expansion valve, evaporator, controls unit, and power panel.
Air Cooled Chiller Parts
What Is An Air Cooled Chiller Condenser And What Do They Do?
Air cooled chiller condensers are horizontal pipes containing the hot refrigerant.
Some thin metal sheets in the vertical axis surround them.
They take away heat from the tubes and distribute them into the air.
This heat is then blown across thin metal sheets and tubes.
Air Cooled Chiller Condenser
What Are The Condenser Fans Of Air Cooled Chillers Used For?
The condenser fans suck air all through the coils of the condenser, coming in through the sides.
They then force out this air to the unit’s top. This air then goes into the atmosphere.
Air Chiller Fan
What Is The Purpose Of The Chiller?
A chiller’s purpose is to transfer heat from one location (a product or process equipment) to the other (usually the air surrounding the facility).
Widely applied in the :
Industrial Process Chiller,
Plastic Industrial Chiller,
Injection Molding Chiller,
Blowing Molding Chiller,
Extrusion Machinery Chiller,
Metal Working Cutting Oils Chiller,
Welding Equipment Chiller,
Chemical Processing Chiller,
Pharmaceutical Formulation Chiller,
Food and Dairy Chiller,
Beverage Processing Chiller,
Vacuum Systems Chiller,
Compressed Air and Gas Chiller,
MRI and Laser Chiller,
Computer Data Center Chiller,
Beer and Wine Fermentation Chiller.
Air Cooled Chiller
Do We Need Water In An Air Cooled Chiller?
Air cooled chillers need hydration. A side of the evaporators of air cooled chillers takes the refrigerant. Water goes into the other side.
A separate water tank is usually present in air cooled chillers for common use.
What Are The Benefits Of A Water-Cooled Chiller Over An Air Cooled Chiller?
- Water-cooled chillers come with a condensing temperature. This temperature is slightly lower compared to air cooled chillers.
- The compressor efficiency of water-cooled chillers is better than that of air cooled chillers.
- Physically, they are smaller
- They are the most economical. So, they offer a simple repair and maintenance
- Lesser noise generated during operation than the air cooled chillers
Water Cooled Chillers
What Is The Maximum Capacity Of An Air Cooled Chiller And Why?
A maximum capacity could mean many things. It could mean cooling capacity, heating power, or chiller power.
Your modular chiller can have capacities of more than 1,000 tons.
For cooling capacity, it could reach 200kw. The chiller’s power could reach 280kw.
Chiller’s maximum heating power could reach 200kw.
Can An Air Cooler Cool A Room?
Yes, air coolers can help in cooling your room.
They are cheap alternatives in the summer season, in contrast to the air conditioners.
Air coolers are cost-effective and work via evaporation.
Blow hot air to pass through the already water-soaked cooling pads.
They can cool more than just a room depending on the size
What Must I Do To Ensure Proper Cooling In A Room?
To ensure you get your room properly cooled, make sure you take care of the following:
- Your room must be well-ventilated
- Make sure you add some ice to the water
- Ensure you saturate the cooling pads before you use them
- Take proper care of the air coolers
What Are The Safety Protections Of Industrial Air Cooled Chillers?
The safety protection of air cooled chillers include devices that help to protect your chiller.
These possible problems include high head pressure, freeze-ups, high motor temperature, short cycle, and low flow, among others.
Protectors include low voltage protector, leakage circuit breaker, and high-temperature protector, among others.
Water Chiller A.C. Contactor
What Are The Common Errors In Air Cooled Chillers?
Some common errors in air cooled chillers include:
Frosting of the compressor suction pipe. This may be because of the improper drainage of the system.
It could also mean the blockage of the system pipeline
Condensation pressure is too high. It happens when your refrigerant is too much.
This makes the temperature of the outside air too high.
If it is too low. This could mean your chiller’s refrigerant is not sufficient.
Also, may mean damage to the compressor of the chiller is damaged.
Excessive heat pressure and excessive suction.
This could happen if the expansion valve is not properly adjusted.
Air Cooled Water Chiller
Does An Air Cooled Chiller Need Water?
Chiller means a machine for water chilling. So, you must use water.
When we mean air-cooled, we mean the chiller’s cooling type of condenser.
For air cooled chillers, the air cools the condenser using the cooling tower.
They surely need hydration. One side of its evaporator takes the refrigerant, while water is taken into the other side.
Can I Find Air Cooled Chillers Having Inbuilt Pumps In The Market?
Yes, you can find air cooled chillers with inbuilt pumps.
They are referred to as swamp coolers, and they can be bought online.
Naturally, chillers are specially designed to solve conditioning or cooling need(s).
Pumps are made to ensure that the brine or chilled water, or cooling water gets to its destination and back.
These pumps do their work consuming very low power and ensuring it completes its task perfectly.
The pump selection and design must be tailor-made with respect to site conditions.
Air Cooled Scroll Chiller
What Could Cause Air Pockets In An Air Cooled Chiller’s Evaporator?
Four things could cause this.
Leakage of a corrosive liquid or steam with high temperature
The leakage could happen in the equipment, flange, and pipeline weld.
It could also happen in other weak links like the expansion joint and sealing filler.
It is caused by cracking due to cold contraction and thermal expansion while starting up and shutting down.
This can also happen due to corrosion and stress impact.
Figure 3: Components of a Chiller
The blockage of the pipeline valve
Crystallization happens with increases in material concentration.
This results in the blockage of the heater, valves, pipelines, etc.
When this happens, the materials will not circulate thereby affecting the smooth operation of evaporation.
Method of troubleshooting for the evaporator’s high temperature
It could be that the expansion valve opening is too large.
Also, mean that there’s too much refrigerant coming into the evaporator.
This can be caused by a very high condensation temperature.
Due to this, there is an increase in the evaporation temperature.
Figure 4: Air cooled Chiller Condenser
Very low evaporation temperature
This could be caused by three things:
- The expansion valve’s opening is too small or blockage of the expansion valve.
- There is not enough refrigerant substituting liquid. Due to this, just a little refrigerant enters the evaporator. This causes part of the surface area not to be able to partake in heat exchange.
- The chilled water’s temperature present in the evaporator is either frozen or too low.
What Does Superheat In Air Cooled Chillers Mean?
Superheat in air cooled chillers refers to when there’s poor heat dissipation in the condenser.
It could also be that the compressor’s efficiency is low, or an increase in the running current.
When its high-pressure pressure increases to 24kg/cm2, this could happen;
The compressor trips off below the high-pressure switch’s protection, which will halt the running of the compressor.
The high-pressure overload caused as a result of poor heat dissipation will reveal the fault indication or fault code.
How Can I Improve An Air Cooled Chiller’s Efficiency?
To improve the efficiency of air-cooled chillers, please follow these:
- Make sure you clean your air-cooled chiller regularly.
- Don’t start and stop the switch button frequently.
- Ensure that there are ventilation and drying in the refrigerator room.
- Don’t stack combustibles or sundries close to your air cooled chiller.
- Check from time to time to ensure the system’s water supply is normal. The system should never experience a water shortage.
- Before you start the air cooled chiller, preheat the compressor. Then you turn on the power supply.
- Clean your chiller’s inner fin heat exchanger regularly. This is to ensure heat exchange.
- Never allow non-professional personnel to dismantle or change the unit. If your unit has any problem, get a professional to check and solve the problem immediately.
- Ensure that no stacking materials or high walls are in front of the chiller’s exhaust fan. This could cause a blockage of the exhaust passage. The refrigeration effect could be affected as well.
- If you will be shutting down the unit for long, try to drain the pipeline’s water. This is to prevent cracking and freezing due to a drop in temperature.
Why Don’t We Have Air Cooled Chillers Larger Than 500 Ton R?
The capacity at which chillers begin to make sense economically is 500 tons.
If you want an air cooled chiller that produces over 500 tons, then you could do it.
This is because the heat transfer surface limits air cooled chillers.
Air cooled chillers reject heat by the air coming in from both sides.
It cools the hot condenser coil which the condenser fans have blown up.
All you need is to install many chillers with many pumps.
At least, this gives you partial capacity in case one of the systems breaks.
How Can I Create An Air Cooled Chiller’s Part Load Performance Table?
It is possible by making use of load banks to stimulate part-load conditions.
Most times, this happens before shipment in the factory when a client requests it.
You can contact our engineer to get the Air Cooled Chiller Catalogue from the air cooled screw chiller machine manufacturer.
GESON industrial air-cooled chiller is a classic product of GESON. It is a new and efficient chiller product developed by GESON’s experienced R&D personnel to meet the needs of various industrial refrigeration.
There are dozens of specifications of GESON industrial air-cooled chillers, and the refrigeration range is from 1300 kcal to 1895000 kcal.
The freezing effluent temperature range is 3℃-25℃.
GESON industrial air-cooled chillers are widely used in various industrial production processes to cool down, such as plastics industry, electronics industry, electroplating industry, food industry, pharmaceutical industry, printing industry)
The compressor adopts a scroll compressor, an imported famous brand compressor from Europe and America, with reliable operation, high efficiency, low failure rate, and low noise.
Using imported Italian water pump, high pressure, high stability, long-lasting durability
Adopt Taiwan Bangpu computer board controller, high display accuracy, and convenient operation
Complete electrical protection system. With phase loss protection. Phase sequence protection. Current overload protection. High and low voltage protection, etc., to ensure the normal operation of the unit.
All the products are tested and passed the factory, and the debugging is successful.
The user only needs to follow the instruction manual, after the unit arrives at the site, connect the electrical circuit and the cold water pipeline, and then it can be put into use.
What is the principle of the laser cutting machine chiller?
Laser cutting machine is a kind of cutting equipment,
It is widely used in industry now.
The air-cooled laser chiller is a chiller that maintains constant temperature, constant pressure and constant flow for the laser cutting machine.
Its market capacity continues to increase at an annual rate of 8%.
Smart laser machines need to be equipped with smarter chillers,
Judging whether the chiller is intelligent depends on whether the chiller has an intelligent “brain”. The thermostat is the thinking and control center of the chiller.
The chiller can be filled with intelligence instantly.
GESON air-cooled type laser chiller has been committed to the design, development and manufacturing of supporting solutions for industrial chillers.
GESON uses dual temperature thermostats, relying on strong R&D and production capabilities.
Give the air-cooled type laser chiller powerful functions,
Let it be full of “wisdom”,
So as to solve the needs of many chiller manufacturers.
The display control is more flexible, safe and reliable;
With Modbus-RTU communication, remote control becomes a reality,
It can be covered into two major functions:
One is to monitor the working status of the chiller (fault self-alarm),
The second is to modify the chiller parameters so that you can control it in real time without on-site work.
In addition, the air-cooled type laser chiller dual temperature dual control system,
One machine can be used for two purposes, saving costs for users, optimizing product image,
Reduce the footprint.
Is this smart and humanized air-cooled type laser chiller what you need?
Air cooled water chiller manufacturers specialize in a common type of liquid chiller. This type of system is designed to be easy to install and use. It is also less expensive than other types of chiller systems. This type of chiller is also easy to maintain and not as demanding when compared to other chillers.
As one of the top air cooled water chiller manufacturers in Asia, we provide convenient installations and maintenance for all our systems. We also provide different solutions to suit your intended use and the required working conditions.
We provide heavy-duty air-cooled water chillers with high ambient temperatures that go up to 60 degrees Celsius. You can also choose between different types of compressor for your air cooled water chiller: screw, scroll, or reciprocating type.
We provide stainless steel heat exchangers if you require cooling for food processing or medical applications. On the other hand, we provide acid corrosion resistance heat exchangers for surface treatment.
Being recognized as one of the most reliable air cooled water chiller manufacturers, we take pride in delivering a comprehensive range of chillers. But we are also able to customize our chiller solutions for different applications and various industries.
Our range of air cooled water chillers enables you to choose from different models. We have air cooled industrial chillers with a cooling capacity range of up to 184 KW. This module comes with a chilled water pump and water tank.
The air cooled central chiller is another option among our range of models. This one has a cooling capacity of up to 928 KW. It is recommended for large-scale uses and comes with its own programmable controller. A central chiller of this size is equipped with a screw compressor.
We can also provide air-cooled low-temperature chillers. The cooling capacity is up to 928 KW with a cooling temperature range of -40 to 5 degrees Celsius. There are plenty of options in terms of cooling medium used such as ethylene glycol, brine, or propylene glycol.
Air cooled chiller comparison
Air-cooled scroll unit VS air-cooled screw unit
Air cooled chiller performance:
Air-cooled Scroll Chiller Compressor Performance:
Using a fully enclosed scroll compressor, the compressor runs smoothly, with low vibration, low noise and long service life.
Air-cooled Screw Chiller Compressor Performance:
The screw compressor is used. During the high-speed rotation and meshing of the screw, the compressor will produce certain vibration and noise. As the working time increases, due to the increase of the rotor gap, the operation efficiency decreases and the power consumption increases.
Air-cooled Scroll Chiller Control Performance
Multiple compressors are operated in parallel, and the number of compressors can be automatically adjusted by the programmable microcomputer controller according to the changes in the terminal air-conditioning load. Therefore, the unit is especially suitable for occasions with low load and large load changes, but the operating efficiency will not change with the load changes, and the energy-saving effect is very obvious. The microcomputer can also automatically record the running time of each compressor to realize the balanced wear function of the compressor.
Multiple compressors operate in parallel and work independently. When individual compressors have operating failures and need to be repaired, they will not interfere with the normal operation of other compressors, so as to ensure that a certain amount of cold and heat sources can be provided in the event of failures.
Air-cooled Screw Chiller Control Performance:
When a single compressor works, the unit adopts stepless capacity adjustment, which will cause the main engine to run at low load, reduce operating efficiency, reduce energy efficiency ratio, and increase operating costs.
When a single compressor is working, even minor failures in the refrigeration system will affect the normal operation of the entire unit and cause the entire air-conditioning host to be in a shutdown state.
Air-cooled Scroll Chiller Installation comparison:
The unit adopts a modular design, which brings more convenience to installation and transportation. The number of modules can be freely combined according to the actual situation of the user. On-site hoisting, handling, and splicing are all very freely.
Air-cooled Screw Chiller Installation comparison:
The unit adopts an integral structure, which is heavy and bulky, and it is very inconvenient for transportation, installation and handling.
Air-cooled Scroll Chiller Maintenance comparison:
Multiple compressors, multiple systems, independent design, fewer system components, light weight, and sufficient space for maintenance. Therefore, maintenance and repair are very convenient.
Air-cooled Screw Chiller Maintenance comparison:
Single compressor, single system, large parts, heavy weight, and very heavy, it is difficult to leave enough space for inspection and repair. Once the equipment fails, troubleshooting is very difficult and it takes a long time.
Air-cooled Scroll Chiller Investment comparison
The one-time investment is small, and it can be installed in batches; if the cooling capacity needs to be expanded, only the modules need to be added, which is very convenient.
Air-cooled Screw Chiller Investment comparison:
Operating cost comparison:
Air-cooled Scroll Chiller Operating cost comparison
The operating efficiency is relatively high under various air-conditioning operating conditions, and the energy efficiency ratio changes little. Therefore, especially for air-conditioned places where the air-conditioning load changes greatly, the energy-saving effect of operation throughout the year is very obvious.
Air-cooled Screw Chiller Operating cost comparison:
When the air-conditioning load changes greatly, the operating efficiency is low and the energy efficiency is relatively small, and the water pump must run continuously. Therefore, the energy-saving effect of the annual operation is very poor. Compared with the air-cooled scroll cold water heat pump unit, the operating cost increases by 15% to 20%.
GESON, the air cooled screw chiller manufacturers, offer a one-stop process cooling solution for your needs.